This very compact steel made manifold consists of a 3 mm thick piping, with a robust layer of black powder electrostatic paint (RAL 9011).
The manifold may be fitted with a standard Grundfos UPS 25 – 55 pump or with an Alpha 2 pump from Grundfos, energy efficient and falling under energy class A.
District heating requires that the manifold is equipped with a bypass valve and a return temperature limiter. A so-called RTL valve in the return pipe.
The manifold bar is equipped with adjustable flow meters, for the calibration of the right volumes in the groups. The manifold is equipped with thermostatizable insertions with a M30 x 1.5 thread, and they can be fitted with most brands of thermal engines for the adjustment of ambient temperature.
The primary connection may be a an upper or a lower connection. In addition, the pump may be placed on the right. The thermostatic valve is double adjustable and, consequently, it may be calibrated, if applicable.
The water temperature is set by using a thermostatic head. This manifold is fitted with an overheating safety thermostat, to prevent the water that is too hot from being pumped in the floor. In the standard mode, this manifold is fitted with a thermometer/manometer.
The group connections are 3/4" Euroconus.