District heating requires that the manifold is equipped with a bypass valve between the supply and return, and that the return temperature can be limited by using an RTL valve.
In addition, this modular plastic made manifold is made of glass fiber reinforced 6.6 polyamide.
Since the modules have double walls, cooling is possible with this manifold without insulating the unit. The condensation level is zero. In addition, the manifold is resistant to glycol mixtures.
This mixing system is equipped with a Grundfos UPS 25-55 pump, but it may also be equipped with an energy efficient Alpha 2 pump from Grundfos. The group connections are 3/4" Euroconus. The manifold bar is equipped with adjustable flow meters, for the accurate calibration of volumetric flows on the groups. The manifold is equipped with built in M30 x 1.5 thermostatic valves. These are suitable for most brands of thermal engines, for a potential adjustment with room thermostats. The water temperature may be set by using a thermostatic head. In the standard mode, this manifold is equipped with a thermometer/manometer and a filling and discharge tap.
The manifold may also be provided with the pump on the right.